Checking HEPA filters?
Steve Carpenter - Cascade Research Assoc.
microbe at clark.pioneer.net
Sun Nov 3 12:18:14 EST 1996
A dry-ice fogger to check for airflow distribution within any HEPA filter
1. Purchase a 2' length of 4" diameter plastic pipe. I use ABS sewer
pipe. Close off one end, being sure to use glue to make it watertight,
and thread the other end so that you can place a screw-on cap on it.
2. Fit the side of the pipe with a plastic or metal tapered pipe fitting
over which you can place a 1/2-5/8" diam, 2-3' length of flexible, clear
3. When you are ready to test, open the cap and put about a half quart to
a quart of hot water. Throw in a good chunk of dry ice. Screw on the
4. Presto! - out comes fog through the clear tubing in the side of the
You can the use the fog in the chamber to see if the air is blowing
properly. If you can access the plenum area above the filter, you may be
able to see leaks through large holes, depending on conditions.
I have use this apparatus to successfully test many HEPA units in cleanrooms.
-Steve Carpenter, Ph.D.
Cascade Research Associates
& Abbey Lane Laboratory
microbe at pioneer.net
More information about the Mycology